Leaks in a heating system can be difficult to locate with our thermal scanner a leak in the heating system can be identified to within 25mm. This service has proven very popular and is a cost effective method to identify leaks.
Contact us if you want to:
Identify a leak in the heating system
Identify under floor heating pipes prior to drilling
Check the efficiency of your heating system
Inspect insulation quality of the heating system
See below for a small small of our leak detection service
Heating System Leak - Apartments
The biro on the floor in the entrance hall of apartment
number 2 indicated in the image is the point where
we detected a leak from the heating system.
This area needs to be opened and repaired to avoid
Under Floor Heating Inspection and Validation
The heating pipe indicated on photograph and the thermal image was operating at 20.7C the remaining areas were at 17.8C.This hot area is where the pipe is too close to the surface.
The layout of the heating pipes indicated was different to the
layout detailed on drawing, they were in a circular layout not
rectangular as per the drawing.
The points detailed in this section are some of the areas of
heating pipe which were closer to the surface than the